After five years of testing, we bring you the results obtained by confronting glass solar panels with a Solbian flexible solar panel, evaluating and analyzing how time affected the devices.
Standard solar panels are rigid, the front protective layer of solar cells is a thick (3-4 mm) tempered ultra-clear glass. This standard solution has been tested for more than 70 years and it is undoubtedly the best to protect cells from weathering and impact, while allowing light to reach them.
Flexible panels cannot use glass, obviously, but polymers. Transparent polymeric films have been always thought as a glass replacement, they are lighter and unbreakable but, whatever the chemical choice, polymers cannot be compared to glass when decades of outdoor resistance are considered. A good compromise can be found nonetheless and in the last 20 years several valid flexible panels appeared on the market, mainly based on thin-film technologies for solar cells: Unisolar amorphous silicon and Global Solar CIGS panels are two well known examples.
The resistance of thin-film flexible solar panels is actually a controversial subject in the field, but also among rigid glass panels, if compared with the boasted 20-25-30 year warranties, some bad stories of early failure are known.
Over ten years ago Solbian started a different path: replacing glass with polymers, but on a panel made of crystalline silicon solar cells. Silicon solar cells are far less sensitive to moisture than thin-film solar devices, but they are more fragile and surely not so bendable.
Solbianflex panels were thus conceived as a compromise, aiming to exploit the high efficiency of crystalline silicon, but without targeting a complete flexibility: panels can be flexed but they are not rollable or pliable in small size. That resulted in an acceptable compromise: Solbianflex panels are used in several markets nowadays.
Before and after the market introduction Solbianflex solar panels have been tested several times, we obtained IEC certifications in 2011 and repeated the trials in 2015, moreover the feedback from thousands of customers has been giving us confidence in our technology, but a real quantitative comparison with the standard, broadly accepted, glass technology was something important for us.
At the beginning of 2013 we had the occasion: a partner company (Ilmed Group) was building a testing solar field to compare different panel technologies and brands. Some of the panels were going to be directly monitored via Enphase Microinvertes and a Solbian panel was added to the group. Five years have passed and now we have the results.
On the roof of a historical building, one of the Nobel factories in Italy, four 60 cell panels have been installed, facing south-southwest, 30 degree slope (left to right):
1. Isofoton ISF235: Monocrystalline, 3 Bus Bar – 235 Wp
2. Jinko JKM240P-60: Polycrystalline, 3 Bus Bar – 240Wp
3. Hanwha SF220-03-1P240L: Polycrystalline, 3 Bus Bar – 240Wp
4. Solbianflex CP 220: Monocrystalline, 2 Bus Bar – 220Wp
…it has to be highlighted that the Solbianflex panel used in this test has around 8% less peak power than the glass panels it is compared to, theoretically the energy yield should be 8% lower compared tot he other panels. It is from our discontinued CP-Series, which has been replaced by the SX-Series which would have 270Wp at the same surface area.
The Solbian panel was glued on the top of an inoperative glass panel, it can be easily recognized in the picture because of the frontal Junction Box.
Tests and results
Since the initial nominal power is different we will be mainly interested in the relative changes through time, anyway a first initial idea of what happened is given by the full life energy production (Feb 12, 2013 – Mar 24, 2018), as shown in the Enphase control panel (Solbian CP220 is the very right panel).
A further interesting step is to look at the same total energy on a different time interval, namely over the last quarter: The Solbian panel is not the less productive anymore. Things are changing.
Let us go back to an overall picture: the average weekly energy produced by the panel during the five year period:
Die Module verhalten sich hier sehr ähnlich – UntThe overall behavior of the four panels is quite similar. It is possible to see the fine details of the different powers, but no hints of larger or lesser degradation of the performance.
A finer analysis can be obtained by looking at the relative performance of the panels. Being one of the panels, the Hanwha, the most performing, we calculated the ratio of the daily energy production of the other three panels compared with the first one. The results in the next picture:
The initial ratio is obviously related to the different power of the panels. Isofoton is declaring 235W, thus its almost 97% ratio, when compared to Hanwha, is inside the power tolerance, the same for Jinko and Solbian: the latter, with its 220W, is precisely at 91% of the Hanwha power.
What is more interesting is the change of ratio with time, while Isofoton and Solbian are decreasing the power gap, the difference between Jinko and Hanwha is increasing, as it was clear from the last data collected (see Fig. 2): since the end of 2017 the Jinko panel is producing less energy than Solbianflex.
Furthermore, if we look at the tendency black lines, it appears that the Solbianflex panel is filling the initial gap more quickly, in other words the Solbian panel shows the smaller power degradation over time.
Honestly, that was unexpected!
Beyond numbers, the visual inspection of the panels gives us some more hints about the behavior during the years.
Solbianflex CP 220 shows the age: the surface is not as glossy as it was right after production, but it retains a good transparency and there is no sign of yellowing. Cells appear in good shape, while the JB, exposed to the sun, has been clearly affected by UV radiation, but -being the panel fully functional- the changes seem restricted to the external surface.
Hanwha panel looks OK, confirming its first of the class position.
Jinko panel, instead, clearly shows inhomogeneous changes of color, iridescent areas are evident. That could be due to deterioration of the encapsulant (moisture?).
The monocrystalline cells of Isofton show clear signs of oxidation on the bus bar. Some moisture entered the panel structure, even if the panel seems not strongly affected by that.
Solbianflex CP 220, a monocrystalline silicon cell panel using an all-polymeric cells encapsulation, has been compared with three similar panels representing the state of the art of standard glass solar panels. Each panel has been monitored via an Enphase microinverter.
The overall behavior of the panels over a 5 year time span is quite similar, the total energy production is consistent with the initial difference in nominal power.
A more detailed analysis shows a performance drift among the panels, with the Hanwha panel leading the group as far as energy production is considered. Isofoton and Solbian panels are slowly closing the gap, namely they are degrading less than Hanwha, while Jinko shows the faster power degradation.
Taking into account both the numerical results and the visual inspection over the examined period, Solbian panel shows the best behavior among the tested samples, fully justifying the 5 year warranty on the Solbianflex range.
The constant development of our product would enable us to realize significantly larger power on the same surface – our SX Series would have 270Wp, the SXX Series even 300Wp compared with even better temperature coefficient and further improved polymers.